El CR1000 consiste en un modulo de almacenamiento y control CR1000M y el panel de alambrado CR1000WP. Este datalogger provee medicion de sensores, mantenedor del tiempo, reducion del tamaño del dato, almacenamiento de datos y programas y funciones de control. Los datos y los programas son almacenados en una memoria permanente y/o memoria RAM. Una bateria de litio respalda la memoria RAM y el reloj de tiempo real. El CR1000 se suspende automaticamente cuando su fuente de poder cae por debajo de los 9,6 V reduciendo la posibilidad de perdida de datos u obtener datos imprecisos. Al datalogger se le pueden conectar diferentes perifericos para aumentar su capacidad de memoria o para comunicarse con el remotamente.
El CR1000 se construyo con la base del CR10 y del CR10X, manteniendose la versatilidad de sus antesesores y mejorando algunas caracteriticas como un puerto RS-232, mas memoria de almacenamiento y mas puertos de comunicacion.
Cuando se utiliza en un sistema de adquision de datos (data-acquisition system) el CR1000 provee funciones de medicion y control. Un sistema completo incluye fuente de poder, caja hermetica, sensores, software de comunicacion y programacion y perifericos de comunicacion.
The CR1000 consists of a measurement and control module and a wiring panel. This datalogger uses an external keyboard/display and power supply. Low power consumption allows the CR1000 to operate for extended time periods on a battery recharged with a solar panel—eliminating the need for AC power. The CR1000 suspends execution when primary power drops below 9.6 V, reducing the possibility of inaccurate measurements.
The CR1000's module measures sensors, drives direct communications and telecommunications, reduces data, controls external devices, and stores data and programs in on-board, non-volatile storage. The electronics are RF shielded and glitch protected by the sealed, stainless-steel canister. A battery-backed clock assures accurate timekeeping. The module can simultaneously provide measurement and communication functions. The on-board, BASIC-like programming language supports data processing and analysis routines.
The CR1000WP is a black, anodized aluminum wiring panel that is compatible with all CR1000 modules. The wiring panel includes switchable 12 V, redistributed analog grounds (dispersed among analog channels rather than grouped), unpluggable terminal block for 12 V connections, gas-tube spark gaps, and 12 V supply on pin 8 to power our COM-series phone modems and other peripherals. The control module easily disconnects from the wiring panel allowing field replacement without rewiring the sensors.
Originally, the standard CR1000 had 2 MB of data/program storage, and an optional version, the CR1000-4M, had 4 MB of memory. In September 2007, the standard CR1000 started having 4 MB of memory, making the CR1000-4M obsolete. Dataloggers that have a module with a serial number greater than or equal to 11832 will have a 4 MB memory. The 4 MB dataloggers will also have a sticker on the canister stating “4M Memory”.
|-NOTE-||Additional specifications are listed in the CR1000 Specifications Sheet.|
|Operating Temperature Range||
|Analog Inputs||16 single-ended or 8 differential (individually configured)|
|Voltage Excitation Terminals||3 (VX1 to VX3)|
|Switched 12 Volt||1 terminal|
|Input Limits||±5 Vdc|
|Analog Voltage Accuracy||±(0.06% of reading + offset) at 0° to 40°C|
|Power Requirements||9.6 to 16 Vdc|
|Real-Time Clock Accuracy||±3 min. per year (Correction via GPS optional.)|
|Internet Protocols||FTP, HTTP, XML, POP3, SMTP, Telnet, NTCIP, NTP|
|Communication Protocols||PakBus, Modbus, DNP3, SDI-12, SDM|
|Battery-backed SRAM for CPU Usage & Final Storage||4 MB|
|Idle Current Drain, Average||< 1mA (@ 12 Vdc)|
|Active Current Drain, Average||
|Weight||1.0 kg (2.1 lb)|
Please note: The following shows notable compatibility information. It is not a comprehensive list of all compatible products.
|LOGGERNET||Version 3.0 or higher|
|PC400||Version 1.2 or higher|
|PCONNECT (retired)||Version 3.1 or higher|
|PCONNECTCE (retired)||Version 2.0 or higher|
|RTDAQ||Version 1.0 or higher|
|VISUALWEATHER||Version 2.0 or higher|
With several channel types, the CR1000 is compatible with nearly every available sensor, including thermocouples, SDI-12 sensors, and 4 to 20 mA sensors (via a terminal input module, such as the CURS100). A custom ASIC chip expands its pulse count, control port, and serial communications capabilities. The CR1000's I/O ports can be paired as transmit and receive, allowing serial communications with serial sensors and devices.
The CR1000 is compatible with all of our CDMs (requires an SC-CPI), SDMs, multiplexers, vibrating-wire interfaces, terminal input modules, and relays.
The CR1000 communicates with a PC via direct connect, Ethernet interfaces, multidrop modems, short-haul modems, phone modems (land line, digital cellular, and voice-synthesized), RF telemetry, and satellite transmitters (Argos, Iridium, and Inmarsat).
Data can be viewed on the CR1000KD Keyboard Display, the CD100 Mountable Display with Keyboard, an iOS or Android device (requires LoggerLink), CD295 DataView II Display, or a user-supplied PDA (PConnect or PConnectCE software required).
Compatible external data storage devices are the CFM100, NL115, and SC115.
The CR1000 and its power supply can be housed in any of our standard enclosures.
Any 12 Vdc source can power the CR1000 datalogger. Power supplies commonly used with the CR1000 are the BPALK, PS150, and PS200. The BPALK provides eight non-rechargeable D-cell alkaline batteries with a 7.5 Ah rating at 20°C.
Both the PS150 and PS200 consist of a sealed rechargeable 7 Ah battery and a charging regulator. Their battery should be connected to a charging source (either a wall charger or solar panel). These two power supplies differ in their charging regulator. The PS150 has a standard regulator and the PS200 has a micro-controller-based smart regulator. The PS200's regulator provides two-step constant voltage charging and temperature compensation that optimize battery charging and increases the battery’s life.
Also available are the BP12 and BP24 battery packs, which provide nominal ratings of 12 and 24 Ah, respectively. These batteries should be connected to a regulated charging source (e.g., a CH100 or CH200 connected to a unregulated solar panel or wall charger).
CRBasic, the CR1000's full programming language, supports simple or complex programming and many onboard data reduction processes. Compatible software includes:
Execution of this download installs the CR1000 Operating System and Compiler on your computer. It also updates the CR1000 support files for the CRBasic Editor.
Note: This OS has crossed the 2 Meg CR1000 size limit for remote download. The OS must be downloaded to the 2 Meg CR1000 via direct connect with the Device Configuration Utility. All OS download methods are supported by the 4 Meg CR1000.
Upgrading from versions prior to version 28 of the Operating System will reset the datalogger’s CPU drive. This is due to a change in the format of the file system from FAT16 to FAT32. In order for the datalogger to operate correctly, as part of the upgrade, the CPU drive is formatted to FAT32. Any programs stored and running from the CPU drive will be lost. It is not recommended to update the datalogger’s Operating System over a remote connection where program control regulates the communication equipment (turning it on or off, etc.). In these cases, an on-site visit and a backup using DevConfig’s backup utility is necessary to update the datalogger’s Operating System.
In all cases where the datalogger is being updated from an Operating System prior to 28, the use of DevConfig’s backup utility is recommended due to the CPU drive being formatted using the new FAT32 format.
A software utility used to download operating systems and set up Campbell Scientific hardware. Also will update PakBus Graph and the Network Planner if they have been installed previously by another Campbell Scientific software package.
Supported Operating Systems:
Windows 10, 8.1, 8, and 7 (Both 32 and 64 bit)
Number of FAQs related to CR1000: 20
Expand AllCollapse All
Recalibration of the CR1000 is recommended every three years.
The CR1000 and CR1000X will be sold concurrently for no less than two years. We anticipate the CR1000 will be retired in December of 2019 and will be supported until December of 2029.
When idle, the CR1000, CR6, and CR1000X consume less than 1 mA @ 12Vdc. Similar to the CR6, the CR1000X has a much faster processor that requires more power when up and running. As such, there will be higher current draws during active measurements, serial communications, or when plugged into a PC via USB or Ethernet.
It may be helpful to think of the CR6 and CR1000X as being built on the same "platform."
Although there are significant additions to the CR1000X program instructions that are not available in the CR1000, in most cases, you can load your program written for the CR1000 to a CR1000X with minor instruction changes. The most notable of the minor instruction changes is in the analog measurement instructions. For more information, see the "Replacing Your CR1000 Data Logger with a CR1000X: What You Should Know" blog article.
CR1000 dimensions with CFM100 or NL115 attached:
9.9 x 4.0 x 2.8 in.
25.2 x 10.2 x 7.1 cm
A practical maximum is to connect one multiplexer per every two control terminals on the data logger. Control terminals can be shared between multiplexers to increase the number of connected multiplexers. Sharing terminals, however, requires more complex wiring and programming. Users who would like to connect more than one multiplexer per every two control terminals are advised to contact a sales or support engineer at Campbell Scientific for assistance.
Yes. The CR1000 is fully programmable to output alarms. The CR1000 can initiate telecommunications such as sending an e-mail or text message, providing audible voice-synthesized information, or calling a pager. The CR1000 can also activate physical alarms, such as sirens and strobes. In this type of installation, a relay device, such as the A6REL-12, is typically used to send a control signal to the alarm device.
The CR1000 can measure analog voltages in the ±5 Vdc range. A voltage divider such as the VDIV2:1 is required to reduce 10 Vdc to an acceptable range. For examples of wiring and programs, see the VDIV10:1/VDIV2:1 manual.
Sending a serial string out one of the data logger COM ports requires at least two instructions. Generally, the SerialOpen() instruction is used to set the characteristics of the communications port, such as baud rate and error detection (for example, 115.2k, N, 8, 1). The instructions SerialOut() or SerialOutBlock() can be used to transmit a specified string. See the CRBasic Editor Help for examples of programs using each of these instructions.